1 Installation diagram
2 Selection instructions
Oil fume purifier selection: It can be directly selected according to the number of stoves of the user, that is, each stove's corresponding air purifier can handle 2000m3 / h.
Induced fan selection: The required fan can be selected according to the fan air volume = purifier air volume.
3 Installation precautions
The purifier can be installed before or after the fan. It is recommended to install before the fan;
When the purifier is installed on the bracket, it should be firmly connected to the bracket;
The connection between the purifier and the exhaust pipe must be sealed;
The purifier can be installed indoors or outdoors, but there should be enough space for maintenance and repair;
The purifier box should be reliably grounded;
During the installation process, it is not allowed to touch the electrode, and foreign objects are strictly prohibited to fall into the purifier;
The electrical connection between the purifier body and the electrical control box is reliable.
4 Instructions for use and precautions
After connecting the AC 220V, 50Hz power supply, the purifier can work. At this time, the work indicator (green) of the electric control box is on, and the purifier itself emits a continuous and stable working sound;
If the reset indicator (red) light flickers occasionally, it is a discharge of the electrode, which is regarded as a normal phenomenon. The purifier can still reset automatically.
If the reset indicator (red) light flashes quickly or stays on for a long time, you can press the reset button. If the red light is still on, turn off the power immediately and open the front door of the purifier. Still unsuccessful, you need to turn off the power and clean the electrodes;
If it still can't work normally after cleaning, please contact professional maintenance personnel for timely inspection;
It is strictly forbidden to open the front door of the purifier and the electric control box while the power is on.